Floods and Gas Controls Warning
NEWS from CPSC
U.S. Consumer Product Safety Commission
Office of Information and Public AffairsWashington, DC 20207
FOR IMMEDIATE RELEASE
April 25, 2001
Release # 01-134 CPSC Consumer Hotline: (800) 638-2772
CPSC Media Contact: Ken Giles, (301) 504-7052
CPSC Warns Flood Victims: Replace All Gas Control Valves, Electric Circuit Breakers, GFCIs, and Fuses That Have Been Under Water
WASHINGTON, D.C. - The U.S. Consumer Product Safety Commission (CPSC) is warning flood victims that all gas control valves, electric circuit breakers, ground fault circuit interrupters (GFCIs), and fuses that have been under water must be replaced to avoid explosions and fires. Even if these safety devices appear to function after being submerged in a flood, they are unfit for continued use and cannot be repaired. They may eventually fail, causing explosions or fires. Other parts of gas and electric appliances that have been submerged such as fans, motors, electric circuits, and venting systems should be evaluated by a qualified technician for continued safe operation. Entire appliances may need to be replaced.
Gas control valves on furnaces, water heaters, and other gas appliances that have been under water must be replaced. Silt and corrosion from flood water can damage internal components of control valves and prevent proper operation. Gas can leak and result in an explosion or fire. Gas control valves that have been under water cannot be salvaged; they must be replaced.
Electric circuit breakers, GFCIs, and fuses that have been submerged must also be replaced because water and silt inside the devices prevent them from performing properly as safety devices. Flood water and silt trapped inside circuit breakers or switches can cause electrical shorting or mechanical malfunctions. The only safe action is to discard and replace circuit breakers, GFCIs, and fuses that have been under water.
CPSC also recommends that consumers replace smoke detectors and carbon monoxide alarms that have been submerged.